EMR , RM and RM use micro- processor technology to perform complex management tasks going way beyond the con- trol of the power factor. The reactive power control relay RM and RM respectively can be .. Model RM /12 Sales Programme Power capacitors for low voltage FRAKO. FRAKO Power Factor Correction Capacitors have a load capacity RM With 12 control contacts. RM With 6 control contacts.
|Published:||9 March 2014|
|PDF File Size:||7.6 Mb|
|ePub File Size:||28.73 Mb|
Read this before commissioning!!! The commissioning and safety information for the power factor correction system should also be observed. Front view a Display for active capacitor stages f LED lights up in setup mode b Display for inductive or capacitive operating status g LED lights up in manual mode h Multifunctional button see operating instructions c Digital display d LED indicates regenerative power i Selection key for manual mode, setup mode or automatic mode e Display for current or historical alarms 4 Figure 2: Rear view j Connection for the current transformer frako rm 2106 Connectors for the control contacts that switch the frako rm 2106.
Introduction Below is a frako rm 2106 overview of the various functions of the device: Working in conjunction with a power factor correction system, the device controls the programmed target power factor by activating or deactivating capacitors.
Power factor control relay / panel-mount / programmable / digital - V | RM - FRAKO
The functions of the control frako rm 2106 are also described in brief in section 1. Troubleshooting information is also provided there. The reactive power control relay RM and RM respectively can be connected in a number of different ways. The main connection methods are described below.
For advanced connection variations see sections 2. The control relay should be disconnected from the mains during frako rm 2106.
- Reactive Power Control Relay RM /12
- Downloads - FRAKO
- Reactive Power Control Relay RM 2106/12
The reactive power control relay is designed for voltage supplies of up to VAC. The reactive power control relay frako rm 2106 installed from the front in a control panel space measuring x mm and is fixed in place using the mounting screws of the front panel.
All information on FRAKO
As accessories protection kit; see section 8 insulated fixing screws are available. These can be used to install the control relay into switchgear cabinets and cubicles of protective class II. Also a sealing ring is part of the protection kit, which must be used when installing the control relay in switchgear cabinets and cubicles of protection class IP Frako rm 2106 keep the load of the current transformer as low as possible, the feed lines should have a adequate cross section.
The pre-assembled fixing clamps ensure frako rm 2106 and secure assembly. Frako rm 2106 electrical connection is created by means of plug-in connectors which are also included in the delivery.
The nominal current in the current transformer path may not exceed 5 A. The outputs of the switching contacts do not have floating potential.
After connection it is necessary to remove the short-circuit jumper on the current transformer, if present. This connection can be used to switch the control relay to a different measuring procedure for frako rm 2106 overcurrent see section 2.
The relevant selection is made in setup mode under